For placing orders, please use the following key:
A customer needs a gas relay of type 80 (CF 38) with a cable gland M20 x 1.5. The switching system is to be provided with two switching elements (magnet contact tubes) designed as NO contacts. The protective device is to operate at two different switching points, namely gas volumes of 200 and 400 cm³. The paint colour of the device should be RAL 7033, and it should be supplied with a miniature ball valve as bleeder valve and without protective covers for the inspection glasses.
Accordingly, the relay ordered has the following
Type code: 80 – 1.25.29AC.44. – 0423
80 = Gas relay of type 80 (CF 38)
1 = M20x1.5: 1 cable gland and 1 dummy plug
25 = Switching system equipped with 2 magnet contact tubes
29AC = with mini ball valve as bleeding valve and without hinged lids for sightglasses
44 = Casing colour RAL 7033 (cement-grey)
04 = Switching point at gas volumes of 200 cm³ and 400 cm³
2 = First switching point = 200 cm³ contact 1
Second switching point = 400 cm³ contact 2
3 = Contact setting of switching system: Contact 1 = NO contact
Contact 2 = NO contact
Please contact us! We are glad to advise you and help with your selection.